Connection of stand-alone option units
Connection of the power regeneration converter (MT-RC) (01800 or more)
When connecting a power regeneration converter (MT-RC), perform wiring securely as shown below. Incorrect
connection will damage the regeneration converter and inverter. After connecting securely, set "1" in
Pr. 30 Regenerative function selection and "0" in Pr. 70 Special regenerative brake duty.
When using the FR-F700 series together with the MT-
RC, install a magnetic contactor (MC) at the input side of
the inverter so that power is supplied to the inverter after
1s or more has elapsed after powering on the MT-RC.
When power is supplied to the inverter prior to the MT-
RC, the inverter and the MT-RC may be damaged or the
MCCB may trip or be damaged.
Refer to the MT-RC manual for precautions for
connecting the power coordination reactor and others.
Connection of the power factor improving DC reactor (FR-HEL)
When using the DC reactor (FR-HEL), connect it between terminals P1-P/+.
For the 01160 or less, the jumper connected across terminals P1-P/+ must be removed. Otherwise, the reactor will not
exhibit its performance.
For the 01800 or more, a DC reactor is supplied. Always install the reactor.
The wiring distance should be within 5m.
The size of the cables used should be equal to or larger than that of the power supply cables (R/L1, S/L2, T/L3).(Refer to page 17)
Inverter input power supply (MC2)
MT-RC power supply (MC1)
1s or more